Many people have heard how good a mini split can be and may want to install a DIY kit but worry about the difficulty.
There are many YouTube videos and websites with lots of talk about mini split systems and installing one.
One thing many post don’t talk about is how difficult an install may be for someone.
With that in mind and after many mini split installs here is my opinion on the topic.
How Difficult Is It To Install a Mini Split?
- Drill a 3-Inch Hole in the Wall
- Running the Line Set
- Pumping Unit Down into a Vacuum
- Testing Line set for Leaks
- Drilling a Hole in the Wall
- Running the Line Set
- Pumping the Unit Down into a Vacuum
- Testing Line Set for Leaks
- Connecting Electrical
For example, a cement wall will be harder than a stucco wall to drill a hole through.
Simply buying the correct sized hole saw and a drill is usually all that’s required.
A line-set will come with any DIY kit and usually will have the ends already flared.
If a unit does not come with the ends flared or the line-set is shortened, a flare tool is used to re-flare the tips.
The line-set runs from the inside unit mounted on the wall to the outside condensing unit.
This is not that difficult; simply take your time when bending the lines going slowly.
The line-set will need to be in a vacuum before the refrigerant is released into the system.
The refrigerant is held in the outside unit that is usually released with an Allen key after everything is finished.
Pumping down the unit requires an HVAC pump and Gauges.
Using them is not that difficult once some basic concepts of how they work is understood.
The gauges are used to measure pressure and hook up to the one port mini split units have.
The pump pulls out all the air and puts the system into a vacuum that it needs to keep the refrigerant clean and uncontaminated.
There can be no leaks in the system, or the refrigerant will leak out.
Some people go to great lengths to make sure there are no leaks with a debate on the best method.
For example, some will use nitrogen to test the system, which I believe is overkill.
When the system is vacuumed down with an HVAC pump, if there are any leaks, it will lose its vacuum.
This is the main way most HVAC techs will test a system.
Gauges and a Pump or hooked up, and the unit vacuumed out.
After it is in a vacuum, the pump is turned off, and the unit is left to sit for 20-30 minutes or longer.
If there is a leak, the unit will lose its vacuum.
If there is no leak, the vacuum will hold, and the refrigerant can be released.
It also will need to be on a breaker to shut off if there is a problem.
Every installation will be different for how the electrical is run.
For example, some may have an electrical panel outside close to where the unit will be and quickly run to the box.
Another install may be on a detached building and need electrical run to it.
A Disconnect box will need to be placed close to the outside unit so it can be shut off or on during maintenance or an emergency.
What Is the Easiest Mini Split to Install?
After installing many mini split DIY kits, the easiest unit to set up was the MRCOOL Mini Split.
I do not think it is difficult to use a vacuum pump or gauges, but there are some nice features about an MRCOOL Mini Split.
- No Need for Vacuum Pump or Gauges
- Comes with Line-Set in a Vacuum.
- Mesh Line Set-that does not Kink
- Leakage Detection
- 120-Volt or 230-Volt Systems Available
The main big feature that makes the MRCOOL Mini Split easy to install is the Quick Connect line-set that comes sealed.
The line-set comes already in a vacuum, with the tips having a seal that is broken when bolted on.
This means there is no need for a vacuum pump or gauges with the line simply bolted onto the condensing unit.
The line-set is also made from a steel mesh material with copper tips that resist kinking, unlike other copper line-sets, which can kink if care is not taken.
This is a big plus for anyone who does not want to buy and learn to use an HVAC vacuum pump and gauges.
MRCOOL DIY unit can also detect a leak with a low coolant alarm.
It also operates on 120-volts which is easier for many to hook up instead of 230-volt system.
*This post contains affiliate links.
Read More About The MRCOOL Mini Split Here on Amazon or eBay
Available Here on Amazon
Mr. Cool units are specifically made for the DIY homeowner to install a mini split as easily as possible.
An installation will need a bracket mounted on a wall for the inside condenser unit and a hole drilled through the wall for the line-set.
The line set goes through the wall and bolts to the outside condenser.
I installed a Mr. Cool mini split in my garage, and it has worked very well both in the winter heating and summer cooling.
Installing most any Mini Split is not difficult for a handy type of person with basic skills.
Personally, I think all units are easy to install and have no problem running electrical or using HVAC vacuum pumps or gauges.
Of course, not having to pump down a unit into a vacuum is convenient and saves time.
So far after installing the many mini split DIY kits available the MRCOOL unit has many features that make it easier to install.
This is only my opinion, so be sure to read the reviews on Amazon, forums, or elsewhere to be sure a unit is a good fit for you.
Have you installed a DIY mini split unit? Let us know how hard or easy the installation was in the comments below.