What is Water Column?
The pressure was applied to one side of the tube from a gas line, and the other side was left open.
How far the gas pressure pushed the water up the open side was measured in inches, and so it was given the name Inches of Water Column.
What Type of Water Column Gauges are There?
- Electronic Manometers
- U-Tube Manometer
- Analog Gas Pressure Readers
Electronic Manometers are the most commonly used tools to measure gas pressure today. They come as dedicated pressure readers or as attachments for some multi meters.
Example Electronic Manometer on Amazon
Fieldpiece Dual-Port Manometer – SDMN5
U-Tube Manometers use the same principles as the first gas pressure readers.
Using water in a U-shaped tube, gas pressure comes into one side and pushes the water up the other side. The difference is measured to give the water column reading. These are not widely used anymore and have been replaced mainly with electronic readers.
Example U-Tube Manometer on Amazon
RadonAway 50017 Easy Read Manometer, Blue
A Magnehelic works by using a diaphragm that is sensitive to pressure and moves in or out depending on the pressure. The diaphragm is connected to a magnet that turns a spiral (helix) into a circle as it moves up or down. The spiral is connected to a needle that will move, giving the pressure.
Analog Magnehelics are still used even though there are electronic replacements. Besides measuring water column, they can also be used to measure fan pressure, blower pressure, air velocity, furnace draft, pressure drop across orifice plates, liquid levels in bubbler systems, pressures in fluidic systems, and filter resistance.
Example Magnehelic On Amazon
Dwyer Magnehelic Series 2000 Differential Pressure Gauge, Range 0-1.0″WC & 0-250 Pa
These are dedicated gas pressure readers that are common. One side is connected to a gas source, and the reading is given out on the gauge.
Example Analog gas pressure reader on Amazon
Robinair 42160 Gas Manifold Pressure Test Kit, 0-35″ Water Column
How Do you Measure Water Column Gas Pressure?
Gas is piped around the country at high pressure and stepped down as it comes into a home. At the point it comes into a home, the pressure will be 7 to 10 inches of Water Column.
This is fed into a furnace gas valve to regulate the correct pressure for the furnace. After the gas goes through a gas valve, it becomes what is called Manifold Pressure. Furnace manufacturers have different pressures, and their furnace manual will need to be looked at for the correct pressure reading. This will usually be between 1 to 3 inches of Water Column.
The gas valve will have a pressure tap located on it. Some gas valves will have a pressure tap on both sides, while some only have one on the furnace manifold side.
- Turn the gas off.
- Locate the pressure tap on the gas valve and unscrew the plug. Then screw in your Manometer.
- Turn the gas back on.
- Turn on the furnace and start it.
- The Manometer will give the reading in Water Column in inches.
- Turn gas off
- Screw back in the gas valve plug using a small amount of pipe dope.
- Turn gas on and check for leaks around the tap screw.
Water Column is used to measure gas pressure with different types of gauges that can be used.
The main types of equipment used to measure the Water Column are Electronic Manometers, U-Tube Manometer, Magnehelic, and Analog gas pressure readers.
If a U-tube or Magnehelic Manometer is used, they will show a vacuum when a furnace starts. This is normal since the inducer motor is pulling a vacuum which will show for a short time at the manifold side of the gas line.
After screwing back in the gas valve tap, be sure to check it for any leaks with soap and water. This is often overlooked, causing problems later on.
Checking the water column pressure is an easy task with the correct safety procedures and tools. Any of the tools mentioned above will read the gas pressure when used correctly.