There are many things that can cause a compressor to stop working.
Below is a list of some common issues to look for when troubleshooting a unit.
Five Reasons an Air Conditioner Compressor Will Not Start
- Start Run Capacitor
- Condensing Fan Motor Failure
- Contactors or Relay
- Electrical Short
- Float Controls
Testing the capacitor is easy enough with an HVAC multi meter. They are also low-cost parts to replace.
Read Here for how to replace an HVAC start Run Capacitor.
When the Fan motor goes bad the compressor will kick on for a short while then stop when the Head Pressure builds up.
Since the heat is not dissipated away from the unit the Amps and heat will build up making the compressor overload and trip off.
If a unit is left On the compressor will cool down and kick back On, going into a bad cycle of running for a short while, over heating and kicking off.
Read Here for How to Replace a Condenser Fan Motor.
Often an Air Conditioner becomes loud when this happens.
This could potentiality damage the compressor since the pressures can get high and pull a lot of Amps.
It uses a low-voltage contactors relay to control the high voltage which can go bad and not allow any voltage through.
A low-voltage thermostat is used to trip a contactor which allows 220 volts into the unit powering it on.
Common problem include pitting or the relay coil winding itself going bad.
Read Here for How To Replace Contactors or Relays.
A bad thermostat or thermostat-wiring will causing a unit not to start.
Be sure to check the thermostat is set on cool and at a low enough temperature to turn on the unit.
HVAC techs often use a jumper wire to trip the unit on were the thermostat wires go into the system.
For example, most air conditioners use the yellow wire to cool and red as the 24DC hot wire.
When the yellow and red wire are jumpered the unit should pull in on the contactor powering on the unit.
If the winding on the Compressor goes bad it will cause the unit to ground out.
The breaker will throw when this happens. It can happen for many reasons such as a small bug got into the unit and the compressor wiring or simply age.
All A/C units need to drain water when it is humid. If the drain pans or hoses become backed up float controls can turn a unit off.
The above are a few of the main problems an HVAC air conditioner or heat pump unit can have.
Each component will need to be tested to find the problem and be replaced.
It can of course simply have a mechanical failure and stop working. If you have run into problems let us know in the comments below.